b'Self-Luminous Exit SignsExit signs stay continuously lit without external power. Illuminated by tritium gas-filled, hermetically-sealed glass tubesConsumes no energy; maintenance free 6"H x 3/4" stroke letters, red polycarbonate faceplate and removable directional arrows Highly durable, vibration and waterproof Hardware included for ceiling, end, or surface mount; hardwaresold separately for pendant mount Listed to UL924; meets codes: NFPA Life Safety Code 101, BOCA, and ICBO Complies with OSHA 29 CFR 1910.37, NFPA Life Safety Code 7.10.4,and NFPA 184.108.40.206Signs contain no electrical components to spark or arcideal for hazardous locations.Ceiling Mount Surface Mount End or Side Mount Pendant Mount (12" standard)Mounting Hardware Included Mounting Hardware Included Mounting Hardware Included Mounting Hardware Sold SeparatelySelf-Luminous Exit Signs Swivel Pendant MountsLife Span ABS Plastic Frame, Price / Each Aluminum Frame, Price / Each Rod Length No. Price / Each8 1/2"H x 14"W x 1"D 8 1/4"H x 12 3/4"W x 1 1/2"D 12" PLS612 $98.6410 Years PLS110 $334.47PLS310 486.20 24" PLS624 107.9320 Years PLS120 620.59 PLS320 865.06 36" PLS636 129.4948" PLS648 140.44Green Polycarbonate Low-Level Signs Faceplate SignsLow-level signs are availableGreen polycarbonate faceplate to meet specific Californiasigns are available to meet Building Code. Order PLS755specific local building codes. and specify lifespan, frameOrder PLS555 and specify material, and quantity. lifespan, frame material and color (black or white), mounting style, and quantity.101 Life Safety Code 7.10.4 Power Source. Where emergency lighting facilities are required.the signs, other than approved self-luminous signs.shall be illuminated by the emergency lighting facilities.220.127.116.11 Listing.Internally illuminated signs shall be listed in accordance with UL924.29 CFR 1910.37 Maintenance, safeguards, and operational features for exit routes. 1910.37(b) Lighting and marking must be adequate and appropriate. (2) Each exit must be clearly visible and marked by a sign reading Exit. (4) If the direction.to the exit.is not immediately apparent, signs must be posted along the exit access indicating the direction of travel.Additionally, the line-of-sight to an exit sign must clearly be visible at all times. (6) Each exit sign must be illuminated to a surface value of at least five foot-candles (54 lux).by a reliable light source and be distinctive in color. Self-luminous.that have a minimum luminance surface value of at least .06 footlamberts (0.21 cd/m2) are permitted. (7) Each exit sign must have the word Exit in plainly legible letters not less than six inches (15.2 cm) high, with the principal strokes of the letters in the word Exit not less than three-fourths of an inch (1.9 cm) wide.127 signkore.com | 780.406.1888All prices are in Canadian Dollars. Freight/Shipping charges may apply to items not in stock. Prices are subject to change without notice.'